Skip to Main Content
The role of boron in flame-retardant treatmentsAuthor(s): S. L. LeVan; H. C. Tran
Source: First International Conference on Wood Protection with Diffusible Preservatives : ... Nashville, Tennessee, November 28-30, 1990. Madison, WI : Forest Products Research Society, 1990.:p. 39-41 : ill.
Publication Series: Miscellaneous Publication
PDF: Download Publication (74 KB)
DescriptionFlame retardants for wood alter the combustion properties of wood to reduce surface flame spread. Flame retardant chemicals cause acid catalyzed dehydration reactions in wood to facilitate the formation of char and reduce the effective heat of combustion, resulting in lower heat release and flame spread. Boron compounds can also form glassy fiis that may inhibit mass transfer of combustible vapors. This paper discusses the role of boron in providing flame retardancy to wood. Different loading levels of borax-boric acid, ranging from O to 20 percent add-on by weight, were applied to Southern Pine. Two types of fire tests were used to evaluate flame retardancy. Clearwood and plywood specimens were tested in the fire tube test and in a heat release rate calorimeter, respectively. It was estimated from fire tests results that loading levels of more than 7.5 percent add-on (3 lb/ft/3/] (48 kg/m/3/] of boraxboric acid are required to meet the ASTM E 84 class I for flame retardant classification.
- We recommend that you also print this page and attach it to the printout of the article, to retain the full citation information.
- This article was written and prepared by U.S. Government employees on official time, and is therefore in the public domain.
CitationLeVan, S. L.; Tran, H. C. 1990. The role of boron in flame-retardant treatments. First International Conference on Wood Protection with Diffusible Preservatives : ... Nashville, Tennessee, November 28-30, 1990. Madison, WI : Forest Products Research Society, 1990.:p. 39-41 : ill.
KeywordsFire retardants, Boron, Chemical modification of wood
- Oxygen index evaluation of fire-retardant-treated wood
- Treated and Untreated foam core particleboards with intumescent veneer
- Room/corner tests of wall linings with 100/300 kW burner
XML: View XML